Jansen Heating & Air Conditioning is known for treating your Terrace Park, OH home like our home. That means we go to great lengths to ensure you are comfortable and get the most out of your HVAC system for the least amount of money.
We have decades of experience working with your Terrace Park, OH neighbors. Find out what they’re saying about us below, then call us to help you with your needs.
for Terrace Park, OH
Our Reviews by City
Nick is great
BRENDEN - Terrace Park, OH
Performed furnace clean and check water is leaking from vent pipe due to incorrect installation need to return with parts to correct issue informed customer would call next week to schedule a time. 1/19/18 returned and replaced vent pipe for furnace under warranty completed clean and check all operations are normal at this time.
Main furnace (basement location) has a clogged secondary heat exchanger confirmed with carrier that the heat exchanger is covered under a parts warranty but customer would still need to pay labor. Changed humidifier pad filter for furnace 1 is clogged need to deliver an fil 20 on monday customer will owe for the filter. Performed clean and check on furnace 2 all operations are normal at this time. Customer is out of 14x20x1 filters plans on purchasing one today. Installed heat exchanger need to retrieve old heat exchanger.
Replaced blown fuse, checked all wiring, could not find the short, cycled unit, all operations ok at this time.
Performed winter maintenance, cycled all equipment, ran all tests needed, tested all safety devices, changed air filter, found unit to be working within specification, all operations ok at this time.
Found humidifier drain was plugged up cleaned drain and informed maintenance needs to be done and water panel needs changed.
Performed clean and check on two furnaces two humidifiers and one boiler changed filters and humidifier pads bled air from boiler system all operations are normal at this time.
Ran new gasoline from the gas meter to the furnace and to the gas fore place. Pressure tested line from meter to gas cocks to verify there are no leaks. Found pressure test to hold pressure without any loss. Left gas cocks off for duke to perform there tests and turn gas back on.
Performed clean and check on 2 furnaces 2 humidifiers and confirmed proper operation of all equipment customer was sent a renewal however unit info contract price and contact information is incorrect sending contract back to Laura to be remade and sent out to bill customer all operations are normal.