In Liberty Township, OH we want you to consider Jansen “Your Heating & Air Conditioning Company”. To earn that right, we continually invest in technician training as well as state-of-the-art technology.
The result is second-to-none repair, replacement and maintenance programs that Liberty Township, OH residents rely on. Read below to see how we’re doing.
for Liberty Township, OH
Our Reviews by City
GENE - Liberty Township, OH
Josh did a wonderful. He got me up & running in less then an hour.
Found system low on charge customer elected to balance system with r22 after reviewing their options. Balanced system with r22 and cycled ac noted that compressor is showing signs of wear and informed customer to be prepared to replace the ac in the near future operations are normal at this time.
Preformed summer maintenance checked all safety devices customer signed up for club membership 2 ac units 1 furnace payed for filters 16 by 25 aprilair. I need to return here at the end of today to put filter in did not have one on truck systems working with in specifications at this time
Found system frozen up due to being low on charge thawed ice off of evaporator coil cycled system installed stop leak and recharged system with 5lbs of R-22 all operations are ok at this time
Arrived at customers house low on air flow found zoning sensor closed had to manually be opened everything working within specifications all operations ok at this time.
Customer stated first floor ac had frozen and there are balancing issues on second floor ac found unit 1 slightly low on charge with service caps off of the unit balanced system and added new caps under warranty as this occurred at last service. Tested and inspected all electrical components and controls cuecked charge on unit 2 rinsed and cleaned ac coils which were clogged and rechecked amp draw and confirmed proper operation of both units customer did not want a maintenance contract at this time.
Preformed summer maintenance on ac checked all safety devices system is working with in specifications at this time talked to wife about club membership said husband will probably call in to enroll
Performed clean and check on gas furnace found inducer assembly with multiple cracks this must be replaced or repaired checked with trane and found that no replacement parts are available for this furnace. Tested and inspected all electrical components and controls found ignitor near failure with an ohm reading of 96.4. Also noted a minor leak near bottom of draft assembly leading toward the secondary heat exchanger this may be from the vent pipe or a seal behind the collector plate which if removed would have to be replaced. Tested humidifier which is operational. Performed combustion analysis which was normal. Furnace is operating at this time.
Performed real estate inspection of ac and furnace checked a.c. refrigerant performed a combustion analysis on the gas furnace found drain pipe on furnace clogged which I corrected tested and inspected all electrical components and controls and confirmed units were in code. All operations are normal at this time. Brushed dirt and debris out of condensor coil and wiped down furnace insured blower wheel was clean.
Found unit frozen up, thawed unit out, found unit to be low on refrigerant, balanced system with 3 pounds of R410A, cycled unit, all operations ok at this time.
Found unit low on R22 refrigerant, balanced system with 4 pounds of R22, cycled unit, all operations ok at this time, quoted new systems for the house. Customer said after vacation he would schedule something.
Found unit low on R410A, balanced system with 3 pounds of R410A, cycled all equipment, all operations ok at this time.
Performed inspection of water heater, furnace and the air conditioning system. Everything is functioning properly an safely. There are no foreseeable issues present with equipment that draws concern. Appears as if all equipment has been properly maintained on a routine basis. However units are well outside of the average life expectancy statistics. Cost evaluation of replacement equipment comparable to what is existing could range $5000-$7500 depending on brand. Anything outside of compararable equipment could range $7000-$13,000 depending on brand, efficiency an comfort level that is desired.
Found furnace with some wiring issues in the low voltage circuit, fixed wiring issues, cycled all equipment, all operations ok at this time