Because of our state-of-the-art technology and skills technicians, Jansen Heating & Air Conditioning is able to provide top-quality repair, replacement and maintenance service to Cincinnati, OH residents.
Read below to learn more about the work we’re doing in the Cincinnati, OH are and what your neighbors are saying about it.
for Cincinnati, OH
Our Reviews by City
Janine - Cincinnati, OH
Very nice young man spent a lot of time looking at unit.
Hot day with AC problems
Darci - Cincinnati, OH
Great service, as always
Sharon - Cincinnati, OH
On time, friwndly, knowledgeable, 100% satisfied
Jansen review of nick
Steve - Cincinnati, OH
Great service, very informative and friendly!
Allison - Cincinnati, OH
Jonathan - Cincinnati, OH
Excellent, prompt, and courteous service. Highly recommended.
Ben - Cincinnati, OH
Everything went perfect!
Maureen - Cincinnati, OH
Nick again was prompt and very efficient in servicing our air conditioning unit.
Mike - Cincinnati, OH
Great as always
Frank - Cincinnati, OH
Back to being cool again!
Robert - Cincinnati, OH
Nick has been to our home before and was familiar with our a/c and furnace. He knew what was needed to get it back in service and was here when he said he would be. Very pleased with him and the service we received.
Prompt and tidy
Connie - Cincinnati, OH
Came on time with a phone call and email beforehand! Good service and well explained.
On time, great job
Donald - Cincinnati, OH
Quick, professional service
Nathan - Cincinnati, OH
The tech was very friendly and professional. Explained things to me and discussed the impact each repair or finding had on the overall efficiency and proper function of our air conditioning.
Quick response and review details of repair.
Jelina - Cincinnati, OH
Fast and friendly service.
Rick - Cincinnati, OH
excelent -customer for many,many years
Wally - Cincinnati, OH
MaryBeth - Cincinnati, OH
Appreciate my service person Zach Austin bring very thorough and communicating his process to me.
Clean and check
Matt - Cincinnati, OH
Dominique was on time and did a good job. Thank you !
best ever service and repair
Ken - Cincinnati, OH
Leslie - Cincinnati, OH
Marsh - Cincinnati, OH
Jansen has always provided excellent service. Their service techs are very courteous, knowledgeable and responds quickly.
Jansen always provides great service
Pam - Cincinnati, OH
Kathy - Cincinnati, OH
Henry - Cincinnati, OH
The technician was great.
Found blown h.v. fuse which I replaced condensor coil was also heavily clogged which I cleaned. Cycled ac and found it low on charge added charge to the system and confirmed all operations are normal at this time please bill customer.
Replaced rewired thermostat sub base thermostat under part warranty. Power surge and transform blew cause power outage
Preformed summer maintenance checked all safety devices changed filter very dirty condensing could cleaned well system is working with in specifications at this time
Performed summer maintenance checked all safety devices system working with in specifications at this time you need ladder to check inside unit
installed new gas regulator and low voltage kill switch
Capacitor was bad replaced system is really old recommend new unit was raining and customer wanted me to check anyway invoice customer bill she said she was told that on the phone
Customer said they had noise problem with outdoor unit i never herd any issues while I was present made sure all scr eww was and bolts were fastened charge was good cleaned unit off for customer as well
Performed summer maintenance cycled all equipment needed checked all safety devices checked filter checked refrigerant charge cleaned condenser coil unit working within specifications all operations ok at this time.
Performed summer maintenance on 2 units cycled all equipment needed checked all safety devices changed filter in attic checked filter in basement check refrigerant in both units and cleaned condenser coils both units working within specifications all operations ok at this time.
Outdoor unit not running think it's bad circuit board needs quote for new circuit board customer have not moved into home yet will be moving in about 2 to 3 weeks
Found Gym condensing unit not started located short in wiring and repairs wires unit also had a bad time delay that would not reset connection replaced time delay cycled unit all operation are okay at this time .
Found blown capacitor which I replaced tested fuses checked for loose wiring and found none, cleaned condensor coil started and cycled ac and confirmed proper operation of equipment all operations are normal at this time.
Performed summer maintenance cycled all equipment needed checked all safety devices changed air filter checked temp drop cleaned condenser coil unit working within specifications all operations ok at this time.
Found exposed wiring behind thermostat cause unit to cut off taped up exposed wiring unit working within specifications all operations ok at this time.
Service call back jumped unit at furnace so ac would run to cool Sanctuary until the part comes in for manufacture. Flip switch on side of furnace to stop units from running
Found condensate pump not operating presses test button on outlet pump now operating within specifications
Found thermostat with bad batteries replaced batteries on thermostat now unit and thermostat are operating normal. Customer has appointment for c&c Monday 10-12
found unit making sparking noise by blower customer had changed out air filter and that was causing unit to freeze blower capacitor was burnt from water dripping when evap was defrosting. Replaced capacitor with new one and unit is no longer making sparking sounds. Unit working within specifications all operations ok at this time.
Found unit not running due to bad high voltage fuses and a bad transformer replaced transformer and fuses cycled system all operations are OK at this time
Found both compressors not working compressor one has something wrong with it I think it might be able to be fixed instead of replace but unfor shore compressor 2 to will not start but did not happen until compressor 1 went out and formed Jim Hull that it's a little out of our range of work and recommend him called train to save money on having the compressor repaired
Found unit not operating with blank thermostat. Checked fuses inside furnace and reset system internally unit is now working within specifications all operations ok at this time.
Found unit not operating on arrival along with blank thermostat. Thermostat is now operating but is not communicating with sub base attached to furnace. Sub base will need to be replaced for normal operation. Part will need to be ordered will set date for replacement.
Found clogged drain line and cleared also noted that the drain was not pitched properly which I corrected all operations are normal at this time.
Found unit had a bad TXV. Need to order part and schedule time to do repair. Replace txv and added vibration insulators on lineset. Everything is working properly at this time.
Found unit not operating upon arrival found that fuses were bad in disconnect box. Fuses have been replaced unit working within specifications all operations ok at this time. Customer had 25 off coupon.