In Milford, OH we want you to consider Jansen “Your Heating & Air Conditioning Company”. To earn that right, we continually invest in technician training as well as state-of-the-art technology.
The result is second-to-none repair, replacement and maintenance programs that Milford, OH residents rely on. Read below to see how we’re doing.
for Milford, OH
Our Reviews by City
Craig/Mary - Milford, OH
Michael - Milford, OH
Tom was very professional & personable. He was willing to diagnose & fix my problem within an hour on a Friday night. He explained exactly what he was doing and taught me better maintenance practices to help my system last longer. He wasn’t the cheapest quote, but he was the first of seven different companies who said he would be here within the hour.
MARY - Milford, OH
Eviltymes3 - Milford, OH
Found condensate pump dirty and float would not lift up cleaned condensate pump cycled system all operations are ok at this time
Started ac checked temp drop and charge which were both normal checked unit size which was on the low side also noted condensor coil was dirty which I washed. Unit is cooling normally at this time. I elected not to charge an overtime fee but explained that this is not typical.
Performed cnc on ac system checked filter and left replacement filter on site tested and inspected all electrical components and controls rinsed and cleaned ac coil all operations are normal at this time.
Preformed summer maintenance on ac checked all safety devices customer could not find uv bulb and I did not have right size pvc to fix clogg 3inch pvc needed customer going to reschedule when they come home from vaction
Found blower was not operating normally contacted carrier and ordered module and motor. Carrier stated this part should arrive at habeggar sharonville on Tuesday. Customer has an extended parts warranty but no labor warranty.
Performed summer maintenance cycled all equipment needed checked all safety devices checked filter checked refrigerant charge cleaned condenser coil found unit to be working within specifications all operations ok at this time. Customer maintenance renewed customer no longer wanted filters on CM.
Checked out all aspects of the HVAC system, cycled all equipment,ran all tests needed, tested all safety devices, checked air filter, could not clean coil due to outside faucet not turned on yet for summer, found unit to be working within specifications, all operations ok at this time.
A/c unit was on low charge. Added 3lbs of R-22 plus stop leak all operations ok at this time
placed rubber grommets on back side of unit
Found unit Frozen and low on R22 refrigerant, turned system off. Sold the customer a new system that goes in on Monday 5/13. System not operating at this time. Greg to bring over supplemental air conditioning tomorrow morning.
Checked out the generator, exercise time is correct, unit had thrown an over crank alarm, reset unit and cycled it, all operations ok at this time.
Performed cnc on ac and cleaned eac renewed customer contract all operations are normal at this time.
Performed spring maintenance on the air conditioning equipment and generator, cycled all equipment,ran all tests needed, tested all safety devices, changed air filters, changed oil and plugs in generator, cleaned condenser coils, found all units to be working within specifications. All operations ok at this time. She wants agreement mailed out.
Performed clean and check on ac system installed new 213 aprilaire filter checked temp drop tested and inspected all electrical components and controls rinsed and cleaned ac coil all operations are normal at this time customer would like price for removal of their humidifier from the system as it is no longer functional they do not wish to replace the humidifier.
Performed clean and check on gas furnace system does not have a humidifier qouted price for installation of new humidifier customer will speak to fiance and may elect to install humidifier. Started furnace checked filter and heat rise performed a combustion analysis tested and inspected all electrical components and controls cleaned flame sensor and condensate trap confirmed proper operation of the gas furnace. Switched system to ac insured refrigerant was balanced checked temp drop tested and inspected all electrical components and controls removed cobwebs from inverter board cleaned ac coil all operations are normal at this time.
Performed clean and check on gas furnace changed filter performed combustion analysis tested and inspected all electrical components and controls added cleaning agent to condensate pump cleaned flame sensor and condensate trap all operations are normal at this time customer did not wish to do ac cnc at this time due to outdoor conditions. Customer is aware they will need to renew when we perform summer cnc.
Upon arrival found system was locked out under ignition lockout tested and inspected electrical components and controls found bad ignitor and replaced cycled furnace all operations are normal at this time. Customer not home at this time please bill customer.
Performed winter maintenance, cycled all equipment, ran all tests needed, tested all safety devices, checked air filter, found unit to be working within specifications, made a recommendation about changing the type of air filter which could be causing the furnace to over heat and also causing the whistling noise that is present, all operations ok at this time.
Removed strainer and cleaned purged fuel lines with co2
Oil furnace shuts down after 5 minutes of operation replaced oil nozzle and filter checked air filter primed pump cycled oil furnace performed combustion analysis all operations are normal at this time.
Performed clean and check on gas boiler tested and inspected all electrical components and controls oiled pump checked temperature differential noted vent pipe had some corrosion insured pipe was sealed informed customer that it may need to be replaced in the future however is operating normally now cycled boiler all operations are normal at this time. Customer would like renewal contracts for his house and 5840 price rd.
Found clogged filter which customer had planned to replace. Removed filter all operations are normal at this time.
Leak checked unit, could not locate a leak at this time, checked refrigerant charge the verify the refrigerant from last week's balancing was still there, added stop leak to the system, cycled unit, all operations ok at this time.
Found unit low on refrigerant causing the electric backup heat to run more than it should which will make the electric bill high, balanced system with 5 pounds of R410 to get it within specifications, all operations ok at this time.
Performed a checkout of equipment. Heat pump is set to run all the time. Told customer I would share my findings with the service manager and see what we come up with. Unit operations are correct at this time.