Because of our state-of-the-art technology and skills technicians, Jansen Heating & Air Conditioning is able to provide top-quality repair, replacement and maintenance service to Cincinnati, OH residents.
Read below to learn more about the work we’re doing in the Cincinnati, OH are and what your neighbors are saying about it.
for Cincinnati, OH
Our Reviews by City
courteous and knowledgeable gentleman -- price was fair
MARILYN - Cincinnati, OH
He came exactly when he said he would, did the job well and answered any questions I had. Jansen is always first-rate and this is no exception.
GREG - Cincinnati, OH
Our technician was very through and informative.
Excellent service! Nick Hursh is very friendly and professional and does great work.
ALICE - Cincinnati, OH
Responded quickly and fixed the problem. Great service.
BETSY - Cincinnati, OH
Nick Hursh was wonderful.
Fall Furnace Check
ROBERT - Cincinnati, OH
Very good service.
JOYCE - Cincinnati, OH
Nice to work with Nick.
Lawrence - Cincinnati, OH
Nick was knowledge and pleasant to work with.
Boiler check up
JAMES - Cincinnati, OH
Nice to work with Nick.
Lawrence - Cincinnati, OH
My furnace was evaluated, but the repair is scheduled for later today.
STEVE - Cincinnati, OH
Nick does a nice job!
Karina - Cincinnati, OH
RAY - Cincinnati, OH
Prompt and good service
BN - Cincinnati, OH
Called in service and someone was out aspromised
Fall service check
KEN - Cincinnati, OH
He fixed it!
Mary - Cincinnati, OH
He fixed the Humidifier today, thank you. I don't know why it wouldn't work though on this expensive newly installed system.
TIm - Cincinnati, OH
SHIRLEY - Cincinnati, OH
Great furnace and generator service
DOUG - Cincinnati, OH
Jansen does an annual inspection of my heating and a/c systems and my generator. Work can be scheduled at my convenience and the workmanship is very thorough and professional.
KAREN - Cincinnati, OH
Very experienced, professional
very friendly and knowlegable.
WALLY - Cincinnati, OH
Always great service
Michael - Cincinnati, OH
Jansen Heating and Air is always there and are very timely and efficient....I have used therefor over twenty five years and have always been satisfied.
Ray is very knowledgeable and thoughtful
ELAINE - Cincinnati, OH
JEFF - Cincinnati, OH
Nick was very responsive and took care of the problem right away.
BILL - Cincinnati, OH
HARRY - Cincinnati, OH
He called and told me he was 15 minutes out and got here withing that time frame. He was courteous and knew what he was doing.
Club membership renewal
Started furnace and performed clean and check on Goodman gas furnace changed filter supplied by the customer inducer motor bearings are worn however motor is not effecting operation of the system at this time but did warn customer that motor could go out in the near future and they may want to consider replacing the furnace at that time given the age of the furnace.
Performed winter maintenance, cycled all equipment, ran all tests needed, tested all safety devices, changed humidifier pad, found unit to be working within specification, all operations ok at this time.
Started furnace checked temp rise insured proper operation of the humidifier customer had already replaced pad left spare on site tested and inspected all electrical components and controls and cleaned flame sensor and condensate trap performed combustion analysis and found co was to high due to a small crack at the heat exchanger checked for co in air stream and found none informed customer that heat exchanger was failing and due to the cost of repairs and the age of the furnace highly recommended that customer replace the system customer had a quote made up from Mike on 8-03-17 Greg is looking into it and will contact customer with further details.
Rebuilt steam generator per Quote cycled system and found that the steam valve was not closing every time so replaced steam valve cycled unit and all operation are ok at this time
Performed winter maintenance, cycled all equipment, ran all tests needed, tested all safety devices, found unit to be working within specification, all operations ok at this time.
Performed clean and check on carrier gas furnace and heat pump customer wanted heat pump lock out raised set heat pump to lock out at 35 degrees. Changed filter performed clean and check on humidifier and showed customer how to set damper for winter or summer all operations are normal at this time.
Installed inducer motor cycled furnace all operations are normal at this time.
Said they were having problems with 3 of the thermostats, found the batteries to be corroded in one and the batteries to be kinda loose in another, changed center thermostat to emergency heat as I think that system isn't keeping up at night cause colder than normal temps in the other areas, tested all operations and checked programming on all three thermostats and found no other issues, gave instructions to have them call back in tomorrow if nothing changed, all operations ok at this time.
Installed new Carrier fan coil and Carrier heatpump. Everything is working properly.
Started furnace changed filter performed clean and check on furnace activated humidifier solenoid valve is leaking heavily and was not able to repair informed customer they need a new solenoid valve customer may also need copper piping replaced. Humidifier not under contract. Returned and replaced solenoid valve and performed clean and check on humidifier replaced pad all operations are normal at this time.
Check out apartment for all radiators are heating But some of the vent dampers were close down not allowing to heat to full capacity Open up all dampeners check water pressure in boiler and temperature setting all operations are OK at this time
Performed clean and check on gas furnace collected contract and payment for maintenance renewal customer has a 213 APRILAIRE media filter. Confirmed proper operation of humidifier all operations are normal at this time.
Found furnace locked out again with sa,etc issue bled air from oil furnace and primed pump finding a solution with nate and will follow up with the customer all operations are now normal at this time.
Performed winter maintenance, cycled all equipment, ran all tests needed, tested all safety devices, changed humidifier pads, found both units to be working within specification, all operations ok at this time.
Found Air curtain not running. unit had burnt electrical connection 2 bad contactors and burnt up transformer. replaced all bad parts. unit is now working but still needs time delay relay
Performed clean and check on electric air handler/heat pump and replaced and tested humidifier pad lowered humidity as house was to humid upon arrival. All operations are normal at this time.
Found unit with a bad secondary heat exchanger. replaced secondary heat exchanger and coupling box Cycled system all operations are ok at this time Customer has a 10 Year P&L
Found boiler with a bad automatic dampner open damper and set to hold unit will work for know but needs damper replaced will send quote to replace damper
Customer stated over phone that boiler was shutting of intermently upon arrival found boiler operating normally, cycled boiler and tested various components found flame sensor was a little weak and cleaned sensor also noted a relay was chatting informed customer that he may have had a flame sense issue or the relay was not sending voltage to the control at some point however all operations are normal at this time. Recommended they call if the issue occurs again.
Found locked out on low pressure switch failure system was full of water removed hoses and drained system found cause was the condensate trap which I cleared and reprimed cycled furnace all operations are normal at this time.
Unit had a failing hot surface ignitor, replaced ignitor and cycled furnace all operations are normal at this time. Emailed receipt please mail receipt as well.
High pressure switch had water causing the system to only run in low fire due to the condensate trap being partially clogged which I cleared cycled the furnace in high fire all operations are normal at this time.